Catchment First Flush Diverter
First-Flush Diverter, Rainwater Harvesting, Rainwater Catchment, , Renewables News DFW, Dallas Fort Worth North Texas North Central Texas Rainwater Catchment, Storage, and Conveyance
First-FlushDiverters Renewable Water for aGreen Homeor Business
DFW Home Radio Archives News/Events Energy Audit Green Building Green Economics Green Remodel Consult Renewable Energy Solar Electricity Solar Hot Water Solar Pool Heating Rainwater Wind DFW Green Building e-Letter DFW Renewable Energy e-Letter DFW Sustainable Living e-Letter
News of Renewable & Alternative Energy
Join our email list here
Renewable Energy& Green ServicesConsultingEconomics of GreenEnergy AuditsGreen BuildingGreen RemodelingRainwater HarvestingRenewable EnergySolar ElectricSolar Hot WaterWind EnergyGlossary
Although larger rooftop debris is collected by the leaf screens, smaller debris such as dust, insect bodies, animal feces, pesticides, etc., is not collected here. A diverter takes care of the smaller debris. The first flush diverter routes the initial flow of water from the harvest surface away from the storage tank.
A hose bibb fixture left slightly open (shown left as option ) or a pinhole drilled at the bottom of the pipe, allows water to gradually leak out. Water from the first-flush diverter be routed to a planted area if desired.
Pipe Diameter Needed to Catch Gallon of Water
Diameter PVC Pipe Length Per Gallon 3" 33" 4" 18" 6" 8"
Although not shown here, equipping the standpipe with ball valve is better. As the chamber fills, the ball floats up, traps the first-flush water, and routes the balance of the water to the tank.
How much water should you divert?
A rule of thumb is to divert a minimum of 10 gallons for every 1,000 square feet of collection surface. However, opinions vary, and the correct answer will also depend upon the number of dry days dust has been allowed to accumulate, the amount and type of debris, the intensity of the rain (see below), the roof slope, and any tree overhang. Even the season of the year can affect the amount of water to divert.
The rain intensity needed to wash your roof is a function of both the roof slope and the intensity of the rain.
Sloped Roof: Needs 0.10 inches of rain per hour.
Flat or Nearly-Flat Roof: Needs 0.18 inches of rain per hour.
A roof washer may also be needed for potable water or if you use the water for drip irrigation.
Once more: Particularly if you intend to use the harvesting system as drinking water, it is very important to consult a professional about your system.
Do you need an energy consultant, energy auditor, green builder, or green remodeler in North Central Texas or the Dallas-Fort Worth area?Are you purchasing or building a home?Ready to add renewable energy?Interested in living more sustainably?Contact Terry JensenFrugal Energy, LLC 972 251-1532 or 817 443-2553 Just have a question or two?Please call. If I can answer withoutseeing your home or business, I will do so at no charge.
Green & Renewable Energy 972 251-1532 or 817 443-2553
Subscribe to free Dallas-Fort Worth Renewable Energy e-newsletter
Sent periodically with home remodeling news and information. Also includes calendar of green events and classes.
Home Contact Consult
Note: The opinions expressedherein are exclusively those of the writers or other participants and do not necessarily reflect theposition of CyberParent. They are not intended to take the place of advice of ahealth, legal, or other professional whose expertise you might need to seek.